نقد و بررسی تخصصی IS200VTURH1BAC
In the simplex application, up to four pulse rate signals may be used to measure turbine speed. Generator and bus voltages are brought into VTUR for automatic synchronizing in conjunction with the turbine controller and excitation system. TTUR has permissive generator synchronizing relays and controls the main breaker relay coli 52G. Shaft voltage is picked up with brushes and monitored along with the current to the machine case.